Section: NUT Manual (8) Updated: 12/24/2010 Local index
oneac - Driver for Oneac UPS equipment
This man page only documents the hardware-specific features of the oneac driver. For information about the core driver, see nutupsdrv(8).
This driver supports Oneac EG and ON UPS equipment with the Advanced Interface. If your UPS is equipped with the Basic Interface card, use the genericups driver.
This driver supports the following optional settings in the ups.conf(5) file:
Change battery test time from the 2 minute default.
This driver supports the following Instant Commands.
Reset the minimum and maximum input line voltage values seen since the last reset or power on.
Start a battery test. The default time is 2 minutes. This time can be set in the
Stops a battery test that is in progress.
Starts a 15 second long simulation of an input power failure.
Eric Lawson <firstname.lastname@example.org>
The core driver:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/
- SUPPORTED HARDWARE
- EXTRA ARGUMENTS
- INSTANT COMMANDS
- SEE ALSO
- The core driver:
- Internet resources:
This document was created by
using the manual pages.
Time: 22:02:05 GMT, April 16, 2011